During routine pressure/leak testing, a fire hose fitting failed at the neck of the stub inserted into the hose. As part of annual testing of the fire hydrant hoses, two crew were assigned to conduct leak testing of the main deck fire hoses. A Number 3 hose (20m x 52mm (2”)) was connected to a fire hydrant valve and nozzle and visual inspections of the hose and valve conducted prior to testing. During the test it was noted that one end of the fire hose had disconnected. The test was stopped, and further investigation was conducted.
What went wrong
Electrolytic corrosion. Initial investigation indicated that this hose appeared to be of a different type from most of the hoses onboard which were made up with an aluminium ‘floating’ flange. This hose had a Storz ‘C’ coupling, which was thought to have flanges fixed to the hose neck. Removal of the rubber sleeve covering the seizing wire revealed conventional Monel seizing wire, and indications were present that water had been retained in the fabric outer sleeve under the rubber sleeve.
Inside the coupling, a steel retaining ring was found buried in the powdery aluminium oxides, confirming that the coupling was in fact the same as the others onboard. But due to corrosion, the floating part was tightly seized on the hose barb shaft.
Investigation of the coupling from the other end of the hose showed no immediate signs of concern. However, there were some small pitting marks evident on the inside of the hose neck and removal of the rubber sleeve showed more indications of corrosion. Attempts to free off the floating flange caused the fitting to fail. It was also noted that corrosion was almost as advanced on this coupling as on the fitting which failed.
- Examine existing fire hose couplings for corrosion, seized floating flanges, and any inability to rotate freely;
- If replacement is required, ensure appropriate fittings are specified – brass may be preferred over aluminium;
- Ensure planned maintenance systems cover appropriate detail for the inspection of fire hose fittings, with specific reference to examination for corrosion;
- Ensure that all personnel involved in the day to day use and maintenance of fire hoses are briefed on the potential issue of electrolytic corrosion.
Members may wish to refer to:
IMCA Safety Flashes summarise key safety matters and incidents, allowing lessons to be more easily learnt for the benefit of all. The effectiveness of the IMCA Safety Flash system depends on Members sharing information and so avoiding repeat incidents. Please consider adding [email protected] to your internal distribution list for safety alerts or manually submitting information on incidents you consider may be relevant. All information is anonymised or sanitised, as appropriate.
IMCA’s store terms and conditions (https://www.imca-int.com/legal-notices/terms/) apply to all downloads from IMCA’s website, including this document.
IMCA makes every effort to ensure the accuracy and reliability of the data contained in the documents it publishes, but IMCA shall not be liable for any guidance and/or recommendation and/or statement herein contained. The information contained in this document does not fulfil or replace any individual’s or Member's legal, regulatory or other duties or obligations in respect of their operations. Individuals and Members remain solely responsible for the safe, lawful and proper conduct of their operations.