We have received a report of a fatality whilst using a fire extinguisher. A worker was using a fire extinguisher to put out a small fire when the extinguisher suddenly exploded, resulting in the person’s death from the flying debris. Part of the extinguisher cracked open when the internal COâ‚‚ cylinder opened (225 psi/17 bar), hitting the user in the chest.
The cause of the incident was corrosion of the cylinder under the rubber protective foot. Water had entered the rubber lining, causing serious corrosion.
We understand that the vendor has distributed a warning to all owners of this type of fire extinguisher stating that the annual inspection should include visual inspection of the bottom of the cylinder after the rubber foot has been removed. Please see the photographs below:
IMCA Safety Flashes summarise key safety matters and incidents, allowing lessons to be more easily learnt for the benefit of all. The effectiveness of the IMCA Safety Flash system depends on Members sharing information and so avoiding repeat incidents. Please consider adding [email protected] to your internal distribution list for safety alerts or manually submitting information on incidents you consider may be relevant. All information is anonymised or sanitised, as appropriate.
IMCA’s store terms and conditions (https://www.imca-int.com/legal-notices/terms/) apply to all downloads from IMCA’s website, including this document.
IMCA makes every effort to ensure the accuracy and reliability of the data contained in the documents it publishes, but IMCA shall not be liable for any guidance and/or recommendation and/or statement herein contained. The information contained in this document does not fulfil or replace any individual’s or Member's legal, regulatory or other duties or obligations in respect of their operations. Individuals and Members remain solely responsible for the safe, lawful and proper conduct of their operations.