A fire main dust cap was blown off by pressure from the line and hit the wall 10m away. The incident occurred when a fire team were checking the firefighting water line filling point connection. The filling point had a camlock fitting and the blank end steel dust cap was in position. The fire team proceeded to release the dust cap by disconnecting the clasps. When the clasp was released, pressure from behind the dust cap blew it off, causing it to hit the wall approximately 10 meters away. This caused minor damage to the wall. There were no injuries to personnel.
What actions were taken? What lessons were learned?
Work was stopped immediately. A thorough inspection of the site was made which identified a few fire ring main lines where the same scenario could occur; these were carefully checked, and any trapped pressure was released. Consideration may be given to the fitting of a drain cock which would allow the release of any residual line pressure prior to cap removal.
Members may wish to refer to:
IMCA Safety Flashes summarise key safety matters and incidents, allowing lessons to be more easily learnt for the benefit of all. The effectiveness of the IMCA Safety Flash system depends on Members sharing information and so avoiding repeat incidents. Please consider adding [email protected] to your internal distribution list for safety alerts or manually submitting information on incidents you consider may be relevant. All information is anonymised or sanitised, as appropriate.
IMCA’s store terms and conditions (https://www.imca-int.com/legal-notices/terms/) apply to all downloads from IMCA’s website, including this document.
IMCA makes every effort to ensure the accuracy and reliability of the data contained in the documents it publishes, but IMCA shall not be liable for any guidance and/or recommendation and/or statement herein contained. The information contained in this document does not fulfil or replace any individual’s or Member's legal, regulatory or other duties or obligations in respect of their operations. Individuals and Members remain solely responsible for the safe, lawful and proper conduct of their operations.