An electrical working foreman was “checking for dead” on control oil pump motor space heaters. It was discovered that the heaters were still live and energized. The heaters were not included in the Lock-out / Tag-out arrangements. After review of the drawings and the load centre breaker schedule, it was determined that the drawing and the breaker schedule were incorrect. The heaters were indicated as one circuit on the drawings and the breaker schedule, but they were traced back to another circuit.
Work was stopped and the LOTO, drawings and breaker schedule were all modified.
What went right
- An increased focus on LOTO during this outage allowed electrical personnel to find the error;
- The electrical working foreman noticed the hazard and it was corrected;
- No-one was harmed.
What went wrong?
- The drawings were incorrect, but as this work was infrequent, it had not been noted previously;
- There was a review of work practices with plant staff to communicate the issue as a result of this alert;
- Ensure all appropriate or possibly relevant electrical equipment is locked out/tagged out;
- Always “check for dead”.
Members may wish to refer to:
IMCA Safety Flashes summarise key safety matters and incidents, allowing lessons to be more easily learnt for the benefit of all. The effectiveness of the IMCA Safety Flash system depends on Members sharing information and so avoiding repeat incidents. Please consider adding [email protected] to your internal distribution list for safety alerts or manually submitting information on incidents you consider may be relevant. All information is anonymised or sanitised, as appropriate.
IMCA’s store terms and conditions (https://www.imca-int.com/legal-notices/terms/) apply to all downloads from IMCA’s website, including this document.
IMCA makes every effort to ensure the accuracy and reliability of the data contained in the documents it publishes, but IMCA shall not be liable for any guidance and/or recommendation and/or statement herein contained. The information contained in this document does not fulfil or replace any individual’s or Member's legal, regulatory or other duties or obligations in respect of their operations. Individuals and Members remain solely responsible for the safe, lawful and proper conduct of their operations.